Product Specifications. • 9th edition approved UL • Capacity of up to 64 panels with zones of programming through software. • Powerful and versatile . FireNET FN/FN UL/FM approved. Expandable loop and connect to other panel. ANALOG ADDRESS FIRE CONTL PAN, Hochiki. Description: Analog Address Fire Contl Panel; Category: Addressable Panels, Fire Control Panels, Fire; UPC.
|Published (Last):||25 March 2018|
|PDF File Size:||9.79 Mb|
|ePub File Size:||3.31 Mb|
|Price:||Free* [*Free Regsitration Required]|
Post Sun Mar 19, 7: I don’t know i am right or wrong. Hlchiki Mon Feb 27, 5: For manual call point placement inside SLC loop what control module is used?
All Rights Reserved From the Firenet installation manual: Can i directly connect sounder base in a SLC loop? The FNSLC can hochikki added at the factory or installed in the field, and mounts within the main control board location as a piggy-back board. You cannot just throw some relays and generic power supplies in the circuit. With 4 amp current we can only connect a few horn strobe. Post Thu Mar 02, So my above think is right or wrong? That’s why i am confused.
Then the horns connected with the hkchiki supply get power from this external power supply when the relay gets power from NAC. Why Hocniki is used? Post here if you need help with something related to fire alarms.
HS Code 85 Import Data Of Vietnam From Singapore in SYS
But I dont want to use som also I want to install many horn within a panel which will work automatically. I do not know if it is acceptable on your particular job site. Search engine Use this form to find things you need on this site.
Post Wed Mar 01, 1: This has to be decided by knowing what is connected to each SOM, how much current hochiii being used, and if that is in the capability of the power supply. Dome Camera p Turbo HD, 2.
That is not legal and could put you and your employer in jeopardy. Suppose i am using 4 SOM in a building. Can you please explain why we use SOM? Post Mon Feb 27, 6: In other words, there is no hard set limit.
Flexible Grooved Coupling – Series. If i use a automatic Sprinklers system then the basic is if there is a fire then detectors detects and send a signal to control panel that there is a fire, then control panel send a signal to notification devices to alarm.
FNHOCHIKI – Analog Addressable Fire Alarm Control Panel, points, expandable, red – EPCOM
Again, the amount of devices depends on the device’s rating, wire gauge, current draw of each device, etc Which devices should connect with this module? That means i 4 loop of NAC devices? In the control panel there is 4 NAC connection points.
Thanks for your reply. Up to devices can be placed on a single SLC loop.
The Fire Panel Forums
Post Sun Mar 05, 6: What is the principle of Supervised Output Module? The interrupt driven Digital Communications Protocol DCP combines maximum communication reliability and fast response to emergency hohiki. The module allows the panel to interface and monitor two-wire conventional detectors or pull stations.
Any power consumed by devices connected to a SOM powered by the panel is also part of that 4 amps. I know that if I use som module then I can conncet many horn within a panel.
User Control Panel Profile Logout.
They can be installed remotely in the building so wire distance and voltage drop issues are reduced. One NAC at 1. Post Sun Mar 05, 3: That means when detectors detects then all horns will sound automatically but not supervised. Also i know that will not supervised. The SOM provides a supervised 24VDC polarity reversing output on the SLC loop most commonly used for audible and visual signaling appliances or triggering a remote notification appliance circuit power expander.